Ecables copper clad aluminum power cable recall
For fixed applications only (all SDI sizes 10 mm – 630 mm and multicores 6 mm – 50 mm).
These units were sold in New South Wales, Queensland, Victoria, and Western Australia from 1 January 2012 to 30 June 2014 by the following traders:
- Ecables Pty Ltd
- Active Elect
- Awesim Elect
- AWM Elect
- Go Elect
- Hastings Elect
- Ideal Elect
- JR Turks
- Lawrence & Hanson
- Middendorp Elect
- TLE Elect
Risk of fire and electric shock
The cable was incorrectly manufactured with incorrectly cross-linked insulation. When the insulation is exposed to temperatures in excess of 50 degrees Celsius, the insulation may become susceptible to mechanical damage exposing live conductors.
All effected parties will be notified directly by Ecables Pty Ltd.
For further information contact:
Ecables Pty Ltd
Telephone: 03 9706 9058
Read others news